CellarPro 4200VSi Cooling Unit #1079
CellarPro's 4200VSi cooling units (2/5 Ton Nominal) are engineered for wine cellars up to 1,000* cubic feet in both commercial and residential wine cellars.
Performance testing shows that this unit maintains optimal cellar temperature and humidity conditions in extreme conditions up to 110F, and are significantly quieter than comparable units from other brands. Visit our Learning Center for data tables, performance charts and product comparisons among different brands.
*Assuming R19 insulation throughout the cellar, 55F inside the cellar and 85F outside the cellar. Cold-side ducting, glass and/or uninsulated walls, extreme humidity, altitude and other factors may affect the sizing calculation.
- CellarPro 4200VSi units are self-enclosed, fully-charged units designed to be installed through-the-wall and sized to fit in between standard wall studs.
- 4200VSi units also can be located remotely from the cellar with the addition of one of our front duct packages. Offered with or without insulated flex ducting, in a choice of configurations for low or high humidity conditions, our front duct packages allow these cooling units to be ducted up to 50 equivalent feet away from the cellar and requires 8-inch (or greater) ducting from start to finish.
- When calculating equivalent feet, each 90-degree turn counts for 8 feet.
- For remote or inaccessible installations, we offer a remote control display kit which is wired to the cooling unit and allows the digital display to be mounted inside or outside the cellar.
- 4200VSi units require fresh air intake at the rear of the cooling unit. If sufficient space does not exist to provide sufficient airflow to the rear of the cooling unit, you may need our rear duct kit.
- 4200VS Series cooling units can be installed completely inside the wine cellar when used with our rear duct kit, which allows you to duct the supply and return airflows from the rear of the cooling unit up to 100 equivalent feet (50 feet per duct).
- For installation in environments below 40F, 4200VSi units require our Compressor Heater (P/N 1727) .
- For installation in environments below 20F down to -20F, we recommend our Fan-Cycling Switch (P/N 6972) combined with our compressor heater.
- The front of the cooling unit should never be exposed to temperatures below 32F.
- A CellarPro cooling unit must always be used in the upright position, and should never be operated on its side or upside down.
- We ship these units strapped to a pallet via common carrier with curbside delivery. Inside delivery is available for an additional charge.
All air-cooled refrigeration equipment requires fresh air intake to dissipate the heat generated by the cooling unit. The fresh air intake CANNOT come from the wine cellar space - it must come from space outside the cellar.
- This unit can be configured to operate in extreme temperature conditions (-20 to 110F). If the unit's location does not provide sufficient room for airflow, you may need to purchase a rear duct kit.
- Dual high-output centrifugal fans come with variable speed settings for your choice of maximum cooling power at the high fan speed, or super-quiet operation (53.7 decibels) at the low fan speed.
- Adjustable humidity control combines a high-output compressor with flexible fan cycles to maintain a recommended level of moisture inside your cellar.
- Extra-large coils generate maximum cooling power inside the cellar.
- Excess condensate is managed with a high-capacity stainless steel drain pan, welded 1/2" drain line and 200W electric heating element with "On/Off" Control.
- Commercial-grade Electrofin coating protects the evaporator coils from leaks and corrosion.
- Intuitive LED display panel mounted on the evaporator with digital programmable thermostat is simple and easy to use. Remote thermostat is available as an upgrade.
- Energy-saver mode, quick-chill mode, and auto-defrost cycle provide convenient solutions to common cellar needs.
- Temperature set point range is 47F to 62F when the cooling unit is properly sized.
- Unit operates with minimal vibrations and less noise than comparable units from competitors.
- Audible and visual alarms and maintenance-needed indicator protect the cooling unit and the wine cellar.
- Common dedicated 15-amp circuit is required to power the unit.
- With dual power sources and a 10-foot power cord, the unit can be plugged into a receptacle from either the front or the rear of the cooling unit, providing flexibility for most installations.
- Our easy-access disposable air filter protects the condenser coils and increases the expected useful life of the cooling unit.
- Adjustable mounting brackets, included as standard equipment, ensure easy installation.
- Removable steel case and refrigerant access valve provides access to the internal components for servicing and repair.
- CellarPro's 5-Year Standard Warranty, the most thorough in the industry, protects the unit against manufacturing defects.
- An optional Extended Warranty (P/N 1836) is available for additional protection.
- ETL Tested and Certified to rigorous UL Standards for safety.
Size: 14 1/10w x 25 1/10d x 19 3/5h (in)
Weight: 155 lbs
115V AC / 60 Hz
- Common dedicated 15-amp circuit is required to power the unit.
- Startup: 42.0 Amps
- Unit Amp Rating: 11.5 Amps (high fan speed)
- Total Watts with Evaporator On / Med Fan: 960
- Total Watts with Evaporator Off / Med Fan: 760
BTUH @ 55F / Decibels:
-Low Fan Speed: 3282 / 54 dBA
-Medium Fan Speed: 3617 / 59 dBA
-High Fan Speed: 3938 / 67 dBA
1/2 Ton Nominal
Capacity: 3938 BTUH @ 55F
Sizing Table: Click here to view sizing table
2 Years (Entire System) / 5 Years (Compressor)
Optional Extended Warranty sold separately.
Click on one of the following links for more information:
- Spec Sheet
- Sizing Table
- Monthly Operating Cost
- Sound Performance
- Cut Sheet
- Cold Side Ducting - Cut Sheet
- Cold and Hot Side - As Ducted
- Installation Diagrams
- Framing Diagram
- Configuration Options
- Owner's Manual
- Product Brochure
- Compressor Heater #1727: protects the unit when installed in environments that drop down to 20F.
- Fan Cycling Switch #6972: supports the unit in temperatures below 20F and as low as -20F when combined with our compressor heater.
- Duct Hoods (Cold Side) (#7408 for low-humidity environments or #7427 for high-humidity environments) and Kits (#1476 for low-humidity environments or #7426 for high-humidity environments): permits the cooling unit to be located remotely, up to 50 equivalent feet away from the cellar using 8" diameter ducting.
- Duct Hood (Hot Side)#7407 and Kit #1113: allows you to install the unit completely inside your cellar or in a small space with limited airflow, up to 100 equivalent feet (50 feet per duct) using 8" diameter ducting.
- Duct Kits are the same as Duct Hoods, and also include 2 x 25-feet of 8-inch insulated (R-6) flex ducting.
Filters & Grills
- Use our filter & grill guide to find the cooling unit filter or duct filter and/or duct grill that is appropriate for your cooling unit.
Remote Thermostats, Displays & Probes
- Networkable Thermostats #27346 and #27310: connect your cooling unit to a networkable, wi-fi enabled thermostat (sold separately). Some limitations apply - read the networkable thermostat description for more information. Includes 10 feet of wiring.
- Remote Display #1603: lets you place the digital panel wherever you want, whether inside or outside the cellar. Includes 10 feet of wiring.
- Bottle Probe #1434: this remote thermostat with a 10-foot cord overrides the thermostat on the face of the cooling unit, and allows it to monitor air or liquid temperatures at various locations inside the cellar.
- Extension cords available in 25-foot (#1780) and 50-foot (#1781) lengths.
DID YOU KNOW?
Nobody protects your wine cellar better than CellarPro Cooling Systems! In the event your cooling unit fails and the failed components are covered by our warranty, we'll send a replacement cooling unit to you per the terms of our Replacement Unit Program
CellarPro Replacement Unit Program
If your CellarPro cooling unit fails and the parts that failed are still covered by warranty, we'll send a replacement cooling unit to you, as follows:
- Your cooling unit must be registered at CellarPro
- Your cooling unit must have been properly sized, installed and maintained
- Your cooling unit may not have been permanently modified, damaged or disfigured
- Replacement units are factory-refurbished cooling units with a similar build date as your original unit
- You are responsible for the shipping cost to send the replacement unit to you and return the original unit to us, and the cost (if any) to remove the original unit and install the replacement unit
- In order to send a replacement unit, we require a deposit, which will be refunded minus shipping costs upon the return and pending the inspection of the original unit
- If the original unit failed due to improper intallation or use, the failure is not covered by warranty and we will deduct the cost of the repairs from the refund of your deposit
A: For installations in environments below 40F down to 20F, we recommend adding our compressor heater (P/N 1727), which is included as standard equipment on all outdoor units. Below 20F, in addition to the compressor heater, we recommend adding our fan cycling switch (P/N 6972)
Can the cooling unit be located in a remote location and ducted to/from the wine cellar?
A: These cooling units can be ducted up to 50 equivalent feet away from the wine cellar when used with our cold-side (front) duct hoods and kits. Remember that cold-side ducting must be insulated and additional load should be added to properly size the required cooling unit.
Does the unit really need a dedicated circuit?
A: First, the background. Unlike our competitors, we build our cooling units with precision expansion valves, not cap tubes, which means that our cooling units aren't limited to a 30F differential between the desired cellar temperature and the ambient temperature. Cooling systems with expansion valves are much more precise than cap tubes, and much more sensitive to low voltage conditions, which is why our units require dedicated circuits. When we say "dedicated circuit", we mean that the circuit shouldn't have any items that require heavy draws of electricity - eg other appliances, vacuum cleaners, big-screen TVs, blow-dryers - on the same circuit as the cooling unit. Lighting, computers or other low-draw items shouldn't be a problem on the same circuit.
Can I install the entire unit inside the cellar?
A: These cooling units can be installed completely inside the wine cellar when used with our hot-side (rear) duct hoods and kits, which allow rear supply and return airflows from a temperature controlled environment OUTSIDE the cellar to be ducted (with insulated ducting to minimize heat transfer inside the cellar) up to 100 equivalent feet (50 feet per duct).
If I don't have sufficient space behind the cooling unit, is that Ok?
A: The rear of the cooling unit generates hot air that must have sufficient space to dissipate, otherwise the unit will recycle its own hot air. The hot air exhaust and/or intake can be ducted to another location with our rear duct hoods and kits, which allow rear supply and return airflows from a temperature controlled environment OUTSIDE the cellar to be ducted (with insulated ducting to minimize heat transfer inside the cellar) up to 100 equivalent feet (50 feet per duct).
Can I use the low fan speed setting on the cooling unit when the unit is ducted?
A: Duct hoods and kits create additional static pressure and therefore require the use of the high fan speed to overcome the additional static pressure.
Ratings & Reviews
CellarPro 4200VSi Cooling Unit #1079
so far so good [1 week]. Had to replace a small unit that wasn't designed for my garage based cellar. Summer heat in the garage can hit 90-94 degrees so they did a good job of finding the right type/size unit for those conditions. I am very pleased that they sent a pre-delivery email telling me to make sure I let the unit rest for 24 hours before testing it. Main reason I like the unit is that if the power goes off and the house generator turns on I don't have to do any resets-- it will work normally. Which is important if you are travelling during summer storm season
I bought this house 3 years ago and it had a wine cellar with a 4200VSI unit that was 4 years old. After 7 years it gave out. After call CellarPro I felt the best option was to replace rather than repair the unit. They offered me a discount for the replacement unit. The new unit was received promptly and in great condition. Since I was replacing an older unit with exactly the same model the swap was very simple. I would give them 5 stars but since my older unit only lasted 7 years, 4 stars is the appropriate rating.
CellarPro VSi Series
by Cellars South -
We are a professional wine cellar designer / builder in the southeast. Climate control systems tend to be the biggest headache in this industry. And over the years we have dealt with most of them, but have made CellarPro our go to choice because of quality, reliability, least amount of maintenance issues and excellent customer service. We have used most all of their systems at one time or another, but the VSI series is what we tend to use the most not only because of its quality, but it’s versatility, ease of installation and cost. It’s a solid product and a solid company. Highly recommend
DIY Cellar Cooler
Local contractors whom I contacted did not seem interested in a smaller existing-cellar cooler system only job. So I did some research and found CellarPro well-recommended, and the 4200VSI unit specs and features seemed an ideal fit for our 800-900 cf of cellar. Unit was in stock and was delivered within days. Came very well packaged and palleted, so the unit was unscathed despite some dings to the outside of the package. Instructions were clear & set up was straight forward and easy, except for actually lifting unit into place of course ... since quality does require some weight in condensers and such. Looks good in the room and appears well built. Unit holds temperature range well and is quiet, we do not even hear the unit when running except in the cellar itself and the adjoining basement exhaust area. This self-contained system is great for a DIY project, if you have the right layout for your cellar and an adjacent space into which to exhaust condenser heat.
Second Time Purchaser
by James -
My first unit lasted almost 7 years to the day. It stopped working at a time of year all the refrigeration specialists are very busy so I decided to purchase a new unit. The new unit fit in the existing hole so the install was very easy and just like the old unit it does a nice job keeping the cellar cool.
wine drinker and cellar builder
fits nice, looks nice and keeps my wine prefect temp
by Vic T
I wanted to say that CellarPro packaging is outstanding. Necessary parts are always provided in their respective packaging.
by Alex R. -
The Quality products and professional but personal service at Cellar Pro is Amazing. They are the only cellar supplier we use and recommend to our customers.
Had to replace my original BreezeAir which lasted maybe one year. Decided to go with CellarPro based on reviews and quality. The unit is not in a desirable location being in the attic on the 7th floor of a condo in Hot Atlanta. However it has performed nicely until the rear fan motor died. Decided to replace with a new CellarPro 4200 since the previous unit was a workhorse for many years. Would highly recommend CellarPro and the customer service are first rate.
Great customer service
by Nick F. -
I had a wine room built as part of a new house. My builder chose the wrong size unit then washed their hands clean of any responsibility. The team at cellar pro were quick to assist even though I was not the one who purchased (builder bought but I paid) and quickly determined I needed a larger unit. I could have gone with the 3200 but decided to have larger 4200 just to be safe. The team walked me through all parts I would need to make my system work. I am happy to report the system is installed and my 300 bottles collection is happy in the 58 degrees chilled cellar. The team also took my smaller unit back and assisted with arranging shipping. To say I am impressed is an understatement. To Ben and Q and the rest of the team thank you.
new wine closet
I just moved into a new home that did not have a wine cellar. I had a Cellarpro 4200VSI in my old wine room and it worked well. I had an issue with the compressor but had it replaced. My new wine room is a bit smaller and I am using the same size unit. This system is ducted at both the front and back of the unit. It is mounted in my attic outside the wine room space. The unit is not in operation yet. I'm impressed with the increase in quality from my last purchase (2010) to now. Customer service has always been responsive & very good.
Much better than Whisperkool
by Braden -
Replaced Whisperkool unit for third time. This last one lasted only 20 months. One before that 3 months. Went with Cellar Pro 4200 CSU unit for a change and am impressed so far with the performance. It easily keeps my 920 ft3 Cellar at 57 at medium fan speed. The installation was easy although some sort of weatherstrip was not included to seal the small gap between unit and frame out.
Came just as described. Jimmy was exceptionally helpful. Took time to make sure it was the right system and that all questions were answered.
Outstanding Unit and Great Customer Support
I have a 1000 bottle cellar in my vacation home in California's Gold Country in Amador County that I built in 2005. It is 100 miles from my primary home in the SF Bay Area. I've replaced 3, yes 3, cooling units that were made in China that I purchased from fill in the blank.Enthusiast.com. Every year they would freeze up and I'd have to drive up and thaw them out. I purchased and installed the CellarPro 4200VSi in October 2016. Here in Northern California, the weather this year has been extremely hot with outside temps exceeding 100 degrees F. This unit has handled the temps without any issue at all. While it automatically circulates air in the cellar every 15 minutes, it only switches into "cooling mode" every couple of hours. My cellar stays at 58 degrees and my electric bill is significantly lower than with the other coolers. What's more, the humidity is about 20% higher than with the other units. I'm sure there is a technical reason for this, but what really matters is the impact on my corks. And I haven't had to make emergency trips to the cellar to deal with failing cooling units and frozen coils. These units are the "real deal". Don't believe the false claims of BTU ratings from others. Customer service has been exceptional. I've called them twice about technical details and they were responsive and straight-forward in their responses. These guys know what they are doing !
by J Fetherston
Replaced a Breezaire, that was only 18 months old, with a Cellarpro. Extremely happy with the unit. It was painful to eat the cost of the Breezeaire but well worth it. The performance difference is remarkable.
by L. Taylor
Very happy with my Cellar Pro. It arrived sooner than expected, was packaged very well, installed easily, and Bryan followed up with me regularly. The unit is performing very well in my cellar. Wish I bought this the first time!
by Ed Wagner
The minute I opened the box I was immediately impressed with the quality of the packaging and upon seeing the unit had great confidence the 4200VSI would do the job. The installation instructions were very clear and straight forward. I recommend following the cut dimensions closely to ensure a tight fit. Also, the unit is heavy so be prepared to have at least two strong individuals when placing in your wall. The unit is very quite and controls both temperature and humidity exactly as needed. I have great confidence this unit will last many years to come.
by Sonray Construction
A very easy to install and excellent product. Great for a DYI or contractor. We have recommended this unit many times. Also the best sales and customer support I have ever dealt with.
4200VSi Review - Cooling Beautifully
by Tofanelli Wines
Installed the 4200VSi last evening. Have to say, out of the box the unit looked less like an air conditioner and more like a piece of serious audiophile sound equipment! Quality,fit, and function is impeccable. Of course it's cooling beautifully! I may have some questions in the coming weeks but for now, hats off to you and CellarPro!
by Robert -
Very easy to install and it cools down the room impressively. Make sure you vent is properly though as it puts out a lot of heat. I'm now sorry I didn't vent this to the outside and easily could have. The first unit that was sent was defective and one other piece of advice is to fire it up and make sure it is blowing cold air (we did fire it up but didn't realize it wasn't actually cooling). Replacement process would have been painless but we had to uninstall the unit. Otherwise very happy.
by Ron B -
A quick note to says thanks for the great service and technical support that I received following my purchase of a 4200VSi cooler. My install was difficult because of location, but with the assistance of Ben A and his technical team, the job went very well. I was particularly impressed when I posted a question to your website via email and had a return message the next day with an offer for me to call Ben on his cell number (on a Sunday, no less). Great equipment, exceptional people and an excellent experience. Thank you!
Love this CellarPro Cooling Unit
by Chris S
Absolutely love this cooling unit. I have a 2,500-bottle wine cellar and I need flawless performance from a unit. This delivers 100%. Best decision I made was purchasing this unit!
My replacement fan was shipped when I was told it would be & contained great directions and a contact if I had a prob. Great company!
Installed this to replace a Breezair unit that failed after 6 years. The 4200Vsi is much heavier than the old one and seems much better built from the outside. It is also more expensive and I hope it's one of those 'you get what you pay for' situations. I really like the 3 speeds and it is also quieter than the old unit. FYI, the unit comes on a pallet and I recommend help to get it unloaded. I have a small tractor with front end loader and that made it easy.
CellarPro 4200 Vsi DIY Install
Replaced a Breezaire unit that leaked water and wouldn't keep my cellar a consistent humidity and was extremely noisey. I mounted this unit in my cellar and used the rear ducting. Temperature and humidity are in the perfect range and I can not hear it running outside of my cellar. I wished I had purchased this one first.