CellarPro 6200VSi-ECX Cooling Unit #14679
CellarPro's 6200VSi-ECX cooling units (3/4 Ton Nominal) are engineered for wine cellars up to 1,900* cubic feet in both commercial and residential wine cellars.
Performance testing shows that this unit maintains optimal cellar temperature and humidity conditions in extreme conditions up to 110F more effectively than similar units from competing brands. 6200VSi-ECX units use energy-efficient EC fans and are significantly quieter than comparable units from other brands. Visit our Learning Center for data tables, performance charts and product comparisons among different brands.
*Assuming R19 insulation throughout the cellar, 55F inside the cellar and 85F outside the cellar. Cold-side ducting, glass and/or uninsulated walls, extreme humidity, altitude and other factors may affect the sizing calculation.
- CellarPro 6200VSi-ECX units are self-enclosed, fully-charged units designed to be installed through-the-wall.
- 6200VSi-ECX units also can be located remotely from the cellar with the addition of one of our front duct packages. Offered with or without insulated flex ducting, in a choice of configurations for low or high humidity conditions, our front duct packages allow these cooling units to be ducted up to 50 equivalent feet away from the cellar using 10-inch ducting.
- When calculating equivalent feet, each 90-degree turn counts for 8 feet.
- For remote or inaccessible installations, we offer a remote control display kit which is wired to the cooling unit and allows the digital display to be mounted inside or outside the cellar.
- 6200VSi-ECX units require fresh air intake at the rear of the cooling unit. If sufficient space does not exist to provide sufficient airflow to the rear of the cooling unit, you may need our rear duct kit.
- 6200VS Series cooling units can be installed completely inside the wine cellar when used with our rear duct kit, which allows you to duct the supply and return airflows from the rear of the cooling unit up to 100 equivalent feet (50 feet per duct).
- For installation in environments below 40F, 6200VSi-ECX units require our Compressor Heater (P/N 1727) .
- For installation in environments below 20F down to -20F, we recommend our Fan-Cycling Switch (P/N 6972) combined with our compressor heater.
- The front of the cooling unit should never be exposed to temperatures below 32F.
- A CellarPro cooling unit must always be used in the upright position, and should never be operated on its side or upside down.
- We ship these units strapped to a pallet via common carrier with curbside delivery. Inside delivery is available for an additional charge.
All air-cooled refrigeration equipment requires fresh air intake to dissipate the heat generated by the cooling unit. The fresh air intake CANNOT come from the wine cellar space - it must come from space outside the cellar.
- Now with energy-efficient EC Fans on both the cold and hot sides, save $300.18 in annual energy costs vs AC fans (assumes 75% runtime and $0.15/kWh)
- This unit can be configured to operate in extreme temperature conditions (-20 to 110F). If the unit's location does not provide sufficient room for airflow, you may need to purchase a rear duct kit.
- Dual high-output centrifugal fans come with variable speed settings for your choice of maximum cooling power at the high fan speed, or quieter operation (57 decibels) at the low fan speed.
- Either the cold side, the hot side or both sides of the cooling unit can be ducted with our duct hoods and kits.
- Adjustable humidity control combines a high-output compressor with flexible fan cycles to maintain a recommended level of moisture inside your cellar.
- Extra-large coils generate maximum cooling power inside the cellar.
- Excess condensate is managed with a high-capacity stainless steel drain pan, welded 1/2" drain line and 100W electric heating element with "On/Off" Control.
- Commercial-grade Electrofin coating protects the evaporator coils from leaks and corrosion.
- Intuitive LED display panel mounted on the evaporator with digital programmable thermostat is simple and easy to use. Remote thermostat is available as an upgrade.
- Energy-saver mode, quick-chill mode, and auto-defrost cycle provide convenient solutions to common cellar needs.
- Temperature set point range is 47F to 62F when the cooling unit is properly sized.
- Unit operates with minimal vibrations and less noise than comparable units from competitors.
- Audible and visual alarms and maintenance-needed indicator protect the cooling unit and the wine cellar.
- With dual power sources and a 10-foot power cord, the unit can be plugged into a receptacle from either the front or the rear of the cooling unit, providing flexibility for most installations.
- Common dedicated 15-amp circuit is required to power the unit.
- Our easy-access disposable air filter protects the condenser coils and increases the expected useful life of the cooling unit.
- Adjustable mounting brackets, included as standard equipment, ensure easy installation.
- Removable steel case and refrigerant access valve provides access to the internal components for servicing and repair.
- CellarPro's 5-Year Standard Warranty, the most thorough in the industry, protects the unit against manufacturing defects.
- An optional Extended Warranty (P/N 1836) is available for additional protection.
- ETL Tested and Certified to rigorous UL Standards for safety.
Size: 16 1/10w x 28d x 22h (in)
Weight: 170 lbs
115V AC / 60 Hz
- Common dedicated 15-amp circuit is required to power the unit.
- Startup: 48.3 Amps
- Unit Amp Rating: 8.4 Amps (high fan speed)
- Total Watts with Evaporator On / Low Fan: 827
- Total Watts with Evaporator Off / Low Fan: 727
BTUH @ 55F / Decibels:
-Low Fan Speed: 5444 / 57 dBA
-High Fan Speed: 5712 / 59 dBA
3/4 Ton Nominal
Capacity: 5712 BTUH @ 55F
Sizing Table: Click here to view sizing table
2 Years (Entire System) / 5 Years (Compressor)
Optional Extended Warranty sold separately.
Click on one of the following links for more information:
- Compressor Heater #1727: protects the unit when installed in environments that drop down to 20F.
- Fan Cycling Switch #6972: supports the unit in temperatures below 20F and as low as -20F when combined with our compressor heater.
- Duct Hoods (Cold Side) (#16667 for low-humidity environments or #16668 for high-humidity environments) and Kits (#14680 for low-humidity environments or #15088 for high-humidity environments): permits the cooling unit to be located remotely, up to 50 equivalent feet away from the cellar using 10" diameter ducting.
- Duct Hood (Hot Side)#19090 and Kit #15092: allows you to install the unit completely inside your cellar or in a small space with limited airflow, up to 100 equivalent feet (50 feet per duct) using 8" diameter ducting.
- Duct Kits are the same as Duct Hoods, and also include 2 x 25-feet of insulated (R-6) flex ducting.
Filters & Grills
- Use our filter & grill guide to find the cooling unit filter or duct filter and/or duct grill that is appropriate for your cooling unit.
Remote Thermostats, Displays & Probes
- Networkable Thermostats #27346 and #27310: connect your cooling unit to a networkable, wi-fi enabled thermostat (sold separately). Some limitations apply - read the networkable thermostat description for more information. Includes 10 feet of wiring.
- Remote Display #1603: lets you place the digital panel wherever you want, whether inside or outside the cellar. Includes 10 feet of wiring.
- Bottle Probe #1434: this remote thermostat with a 10-foot cord overrides the thermostat on the face of the cooling unit, and allows it to monitor air or liquid temperatures at various locations inside the cellar.
- Extension cords available in 25-foot (#1780) and 50-foot (#1781) lengths.
DID YOU KNOW?
Nobody protects your wine cellar better than CellarPro Cooling Systems! In the event your cooling unit fails and the failed components are covered by our warranty, we'll send a replacement cooling unit to you per the terms of our Replacement Unit Program
CellarPro Replacement Unit Program
If your CellarPro cooling unit fails and the parts that failed are still covered by warranty, we'll send a replacement cooling unit to you, as follows:
- Your cooling unit must be registered at CellarPro
- Your cooling unit must have been properly sized, installed and maintained
- Your cooling unit may not have been permanently modified, damaged or disfigured
- Replacement units are factory-refurbished cooling units with a similar build date as your original unit
- You are responsible for the shipping cost to send the replacement unit to you and return the original unit to us, and the cost (if any) to remove the original unit and install the replacement unit
- In order to send a replacement unit, we require a deposit, which will be refunded minus shipping costs upon the return and pending the inspection of the original unit
- If the original unit failed due to improper intallation or use, the failure is not covered by warranty and we will deduct the cost of the repairs from the refund of your deposit
A: You should always use Sensible BTUH* when comparing different brands of cooling units, and when sizing a cooling unit for your wine cellar. Every cooling unit produces a certain amount of Total BTUH, which is the sum of Sensible BTUH (lowers the temperature) and Latent BTUH (lowers the relative humidity). Because our goal is to cool wine cellars while preserving humidity, wine cellar cooling units should have high Sensible BTUH and low Latent BTUH. The relationship between Sensible and Latent BTUHs is know as SHR (Sensible Heat Ratio), which is calculated as Sensible BTUH/Total BTUH. The SHR for CellarPro cooling units is greater than 90%, which means that CellarPro units provide maximum cooling power without stripping out humidity from the cellar environment.
*CellarPro Sensible BTUHs are calculated assuming 55F cellar temperature, 60% relative humidity and 95F ambient for all units except 1800 units (85F ambient).
How cold can the temperature be where the cooling unit is installed?
A: For installations in environments below 40F down to 20F, we recommend adding our compressor heater (P/N 1727), which is included as standard equipment on all outdoor units. Below 20F, in addition to the compressor heater, we recommend adding our fan cycling switch (P/N 6972)
Does the unit really need a dedicated circuit?
A: First, the background. Unlike our competitors, we build our cooling units with precision expansion valves, not cap tubes, which means that our cooling units aren't limited to a 30F differential between the desired cellar temperature and the ambient temperature. Cooling systems with expansion valves are much more precise than cap tubes, and much more sensitive to low voltage conditions, which is why our units require dedicated circuits. When we say "dedicated circuit", we mean that the circuit shouldn't have any items that require heavy draws of electricity - eg other appliances, vacuum cleaners, big-screen TVs, blow-dryers - on the same circuit as the cooling unit. Lighting, computers or other low-draw items shouldn't be a problem on the same circuit.
Can the cooling unit be located in a remote location and ducted to/from the wine cellar?
A: These cooling units can be ducted up to 50 equivalent feet away from the wine cellar when used with our cold-side (front) duct hoods and kits. Remember that cold-side ducting must be insulated and additional load should be added to properly size the required cooling unit.
Can I install the entire unit inside the cellar?
A: These cooling units can be installed completely inside the wine cellar when used with our hot-side (rear) duct hoods and kits, which allow rear supply and return airflows from a temperature controlled environment OUTSIDE the cellar to be ducted (with insulated ducting to minimize heat transfer inside the cellar) up to 100 equivalent feet (50 feet per duct).
If I don't have sufficient space behind the cooling unit, is that Ok?
A: The rear of the cooling unit generates hot air that must have sufficient space to dissipate, otherwise the unit will recycle its own hot air. The hot air exhaust and/or intake can be ducted to another location with our rear duct hoods and kits, which allow rear supply and return airflows from a temperature controlled environment OUTSIDE the cellar to be ducted (with insulated ducting to minimize heat transfer inside the cellar) up to 100 equivalent feet (50 feet per duct).
Can I use the low fan speed setting on the cooling unit when the unit is ducted?
A: Duct hoods and kits create additional static pressure and therefore require the use of the high fan speed to overcome the additional static pressure.
Ratings & Reviews
Replace BreezAire with 6200VSI CellarPro
Arrived in good shape, no issues there. So far it’s running fine. I’m happy with your unit at this point. It runs much quieter than the BreezAire I replaced with this Unit. Had some breaker popping issues at first but had an electrician take a look at the breaker which he replaced and that solved the problem.
by MA Cantrell Heating & Air
I have been installing cellar pro units for 6-7 years and this is the first unit that I have had to replace parts on. Very good units
Effective but does not fit in standard stud opening
The unit arrived in good condition in about a week. It is heavy as advertised and appears to be well made from the outside (I didn't open the cover). The install was not quite as easy as I may have liked, the installation information should add about another 1/4" to 3/8" for the rough opening to ensure a smooth fit. My install was in an existing cellar which makes it a bit trickier to get your rough opening to the exact size. Also be very aware that this larger unit will not fit in a standard 16" on center stud wall. Cellar Pro does note this in the description online, however I asked the agent on the phone and was told that it will fit a standard stud pocket. So if you installing in old construction you may be in for a lot more work. This unit is not very quiet either, you will know it is running. Now for the important part, I am very happy with the unit and I would choose it again. Other than than a little misinformation on the size (which I could have verified myself online) the staff were very helpful. It has cooled my cellar and is maintaining it just where I want.