4200 220V: Sizing Table - Wine Cellars 14-42 cubic meters
13°C Cooling Capacity1
15°C Cooling Capacity1
The table is shaded to show how the 4200 cooling unit will work at 15°C in a 220V / 50Hz environment using various fan speeds under various thermal loads. The thermal loads are derived from assumptions about the size of the cellar; the R-value in the six cellar surfaces (ie walls, floor and ceiling) and the ambient temperature outside the cellar.
In 220V / 50Hz environments, CellarPro 4200 wine cooling units are designed to maintain 15°C temperatures in wine cellars up to 28 cubic meters with adequate insulation, and can be operated with the condenser exposed to conditions up to 46°C. For more information, click on our 4200VS performance and test data.
(1) The thermal loads above are calculated based on the R-Values shown for all walls and ceiling, and a concrete floor. Lower R-Values in the cellar (eg from glass doors) will increase the thermal load on the wine cellar and will require the cooling unit to operate at higher fan speeds. Warmer climates require higher insulation to enable the cooling unit to operate at lower fan speeds. To be certain that the thermal load won't exceed the capacity of the cooling unit, email your wine cellar specifications to us and we'll be glad to assist you.
Cells shaded blue indicate loads that exceed the capacity of the cooling units shown in this table.