CellarPro 6000S-EC Split System #1764
CellarPro's 6000S-EC cooling units (1/2 Ton Nominal) are engineered for wine cellars up to 1,500* cubic feet in both commercial and residential wine cellars.
Performance testing shows that this unit maintains optimal cellar temperature and humidity conditions in extreme conditions up to 110F more effectively than similar units from competing brands. 6000S-EC units use energy-efficient EC fans in the evaporator and are significantly quieter than comparable units from other brands. Visit our Learning Center for data tables, performance charts and product comparisons among different brands.
*Assuming R19 insulation throughout the cellar, 55F inside the cellar and 85F outside the cellar. Cold-side ducting, glass and/or uninsulated walls, extreme humidity, altitude and other factors may affect the sizing calculation.
- CellarPro 6000S-EC units are designed to be installed with the evaporator inside the cellar, and the condensing unit in a remote location.
- Our Split refrigeration systems offer a choice of wiring:
- The Condensing unit can be electronically controlled by and wired to the Evaporator (single power source on the Evaporator side). This configuration allows the Condensing unit to be used in temperatures down to 20F with the addition of our compressor heater, or down to -20F with the addition of our fan cycling switch AND compressor heater. This configuration requires a 15-amp dedicated circuit breaker for 3000S and 4000S systems, and a 25-amp dedicated circuit breaker for 6000S-EC and 8000S systems.
- The Condensing unit can be controlled by a Solenoid valve (dual power source, one each to the Evaporator and Condensing units.) This configuration allows the Condensing unit to be used in temperatures down to 20F with the addition of our compressor heater. This configuration requires the evaporator to be wired to a 15-amp circuit breaker, and the condensing unit to be wired to a dedicated 15-amp circuit breaker for 3000S and 4000S systems, a dedicated 20-amp circuit breaker for 6000S-EC systems, and a dedicated 25-amp circuit breaker for 8000S systems
- 6000S-EC evaporators cannot be ducted from a remote location and must be located inside the cellar.
- When the control panel is difficult to access, we offer a remote control display kit which is wired to the cooling unit and allows the digital display to be mounted inside or outside the cellar.
- The condensing unit requires 12 inches of unobstructed space in front of the coils, and requires approx. 600-700 CFM of ventilation when installed in a confined space.
- For outdoor installations, we offer an outdoor hood to protect the condensing unit from weather. All outdoor hoods include a compressor heater.
- The evaporator should never be exposed to temperatures below 32F.
- Access to the left and right side of the evaporator unit is required for installation.
- All split systems must be installed and charged on site by a qualified HVAC professional. Line-set equivalent feet must be calculated in accordance with ASHRAE guidelines; refer to our Line Sizing Chart for more information.
- A CellarPro cooling unit must always be used in the upright position, and should never be operated on its side or upside down.
- We ship these units strapped to a pallet via common carrier with curbside delivery. Inside delivery is available for an additional charge.
- To activate your warranty, you must complete and return our Installation Checklist.
Our cooling units are designed to be used in properly-constructed wine cellars that are adequately insulated, airtight and sealed with a vapor barrier. In improperly-constructed cellars, the cooling unit will create excess condensation, leading to damage and premature failure of your cooling unit (not covered by warranty).
All air-cooled refrigeration equipment requires fresh air intake to dissipate the heat generated by the cooling unit. The fresh air intake CANNOT come from the wine cellar space - it must come from space outside the cellar.
- Now with energy-efficient EC Fans on the cold side, save $107.42 in annual energy costs vs AC fans (assumes 75% runtime and $0.15/kWh)
- This unit is designed to separate the heat and noise from the condensing unit from interior living spaces, and can be configured to operate indoors or outdoors in extreme temperature conditions ranging from -20 to 110F.
- Our Evaporators are built with high-output centrifugal fans which include variable speed settings for your choice of maximum cooling power at the high fan speed, or quieter operation (53.7 decibels) at the low fan speed.
- Adjustable humidity control combines a high-output compressor with flexible fan cycles to maintain a recommended level of moisture inside your cellar.
- Extra-large coils generate maximum cooling power inside the cellar.
- Excess condensate is managed through a 1/2" drain line that exits from a choice of knockouts in the evaporator.
- Commercial-grade Electrofin coating protects the evaporator coils from leaks and corrosion.
- Intuitive LED display panel mounted on the evaporator with digital programmable thermostat is simple and easy to use. Remote thermostat is available as an upgrade.
- Energy-saver mode, quick-chill mode, and auto-defrost cycle provide convenient solutions to common cellar needs.
- Temperature set point range is 47F to 62F when the cooling unit is properly sized.
- Unit operates with minimal vibrations and less noise than comparable units from competitors.
- Audible and visual alarms and maintenance-needed indicator protect the cooling unit and the wine cellar.
- Common dedicated 20-amp circuit (valve control) or 25-amp circuit (electronic control) is required to power the unit.
- Adjustable mounting brackets are included as standard equipment, and multiple knockouts and access points ensure easy installation.
- Factory-installed Expansion Valve and Liquid Line Solenoid Valve (optional) ensure maximum operating precision and range.
- Removable steel case and refrigerant access valve provides access to the internal components for servicing and repair.
- Sight Glass and Liquid Line Filter/Drier are included for easy installation and maintenance.
- Oversized Receiver allows for long line sets up to 100 equivalent feet and up to 30 vertical feet.
- Auto-reset high-pressure switch protects the system by interrupting power to the compressor when system pressure is too high.
- Evaporator and Condensing Unit are factory-pressurized and shipped with dry nitrogen to ensure leak-free installation.
- CellarPro's 2-Year/5-Year Warranty, the most thorough in the industry, protects the unit against manufacturing defects.
- An optional Extended Warranty (P/N 7528) is available for additional protection.
- ETL Tested and Certified to rigorous UL Standards for safety.
Size: 30 3/8w x 14 3/8d x 13 1/4h (in)
Weight: 185 lbs
115V AC / 60 Hz
Condensing Unit Dimensions:
- 54 lbs
- 13.9w x 18.9d x 11.9h
Evaporator Unit Dimensions:
- 68 lbs
- 30.4w x 14.4d x 13.2h
-Common dedicated 20-amp circuit (valve control) or 25-amp circuit (electronic control) is required to power the unit.
- Startup: 53.0 Amps
- Unit Amp Rating: 12.6 Amps (high fan speed)
BTUH @ 55F / Evaporator Decibels
- Low Fan Speed: 4311 / 54 dbA
- Med Fan Speed: 4880 / 58 dbA
- High Fan Speed: 5046 / 66 dbA
- 3/4 Ton Nominal
Condensing Unit Decibels
- Indoor: 65
- Outdoor: 63
Capacity: 5046 BTUH @ 55F
Sizing Table: Click here to view sizing table
2 Years (Entire System) To activate your warranty, you must complete and return our Split Installation Checklist.
Optional Extended Warranty sold separately.
Click on one of the following links for more information:
- Spec Sheet
- Sizing Table
- Monthly Operating Cost
- Evaporator Cut Sheet
- Condensing Unit Cut Sheet
- Evaporator Mounting Instructions
- Line Sizing Chart
- Configuration Options
- Wiring Diagram - Dual Power/ Valve Control
- Wiring Diagram - Single Power / Electronic Control
- Refrigerant Piping Diagram
- Refrigerant Piping Handbook
- Owner's Manual
- Product Brochure
- Installation Checklist
- Compressor Heater #35605: protects the unit when installed in environments that drop down to 20F. Included
- Fan Cycling Switch #6972: supports the unit in temperatures below 20F and as low as -20F when combined with our compressor heater.
- Outdoor Hood #2009: allows you to install the condensing unit outdoors; all outdoor hoods include a Compressor Heater #1727.
Filters & Grills
- Use our filter & grill guide to find the cooling unit filter or duct filter and/or duct grill that is appropriate for your cooling unit.
Remote Thermostats, Displays & Probes
- Networkable Thermostats #27346 and #27310: connect your cooling unit to a networkable, wi-fi enabled thermostat (sold separately). Must be ordered at the same time that the equipment is ordered. Other limitations apply - read the networkable thermostat description for more information. Includes 10 feet of wiring.
- Remote Display #1603: lets you place the digital panel wherever you want, whether inside or outside the cellar. Includes 10 feet of wiring.
- Bottle Probe #1434: this remote thermostat with a 10-foot cord overrides the thermostat on the face of the evaporator, and allows it to monitor air or liquid temperatures at various locations inside the cellar.
- Extension cords available in 25-foot (#1780) and 50-foot (#1781) lengths.
DID YOU KNOW?
Nobody protects your wine cellar better than CellarPro Cooling Systems! In the event your cooling unit fails and the failed components are covered by our warranty, we'll send a replacement cooling unit to you per the terms of our Replacement Unit Program
CellarPro Replacement Unit Program
If your CellarPro cooling unit fails and the parts that failed are still covered by warranty, we'll send a replacement cooling unit to you, as follows:
- Your cooling unit must be registered at CellarPro
- Your cooling unit must have been properly sized, installed and maintained
- Your cooling unit may not have been permanently modified, damaged or disfigured
- Replacement units are factory-refurbished cooling units with a similar build date as your original unit
- You are responsible for the shipping cost to send the replacement unit to you and return the original unit to us, and the cost (if any) to remove the original unit and install the replacement unit
- In order to send a replacement unit, we require a deposit, which will be refunded minus shipping costs upon the return and pending the inspection of the original unit
- If the original unit failed due to improper intallation or use, the failure is not covered by warranty and we will deduct the cost of the repairs from the refund of your deposit
A: You should always use Sensible BTUH* when comparing different brands of cooling units, and when sizing a cooling unit for your wine cellar. Every cooling unit produces a certain amount of Total BTUH, which is the sum of Sensible BTUH (lowers the temperature) and Latent BTUH (lowers the relative humidity). Because our goal is to cool wine cellars while preserving humidity, wine cellar cooling units should have high Sensible BTUH and low Latent BTUH. The relationship between Sensible and Latent BTUHs is know as SHR (Sensible Heat Ratio), which is calculated as Sensible BTUH/Total BTUH. The SHR for CellarPro cooling units is greater than 90%, which means that CellarPro units provide maximum cooling power without stripping out humidity from the cellar environment.
*CellarPro Sensible BTUHs are calculated assuming 55F cellar temperature, 60% relative humidity and 95F ambient for all units except 1800 units (85F ambient).
What's the difference between a split system and "through the wall" or "self-contained" systems?
A: Split systems are "split" into two parts: the cold side (evaporator) which usually is installed inside the cellar, and the hot side (condensing unit) which is installed away from the cellar. The benefit of having this split is that the heat and noise from the condensing unit can be located far away from living spaces where it won't interfere with day-to-day life.
Are split systems more difficult to install than self-contained systems?
A: Yes. Split systems require installation by a licensed HVAC technician, whereas a self-contained unit can be mounted through-the-wall and is shipped fully charged and operational out of the box.
What's the difference between valve control and electronic control? Which is better?
A: The biggest difference between valve and electronic control is that, with electronic control, the condensing unit receives power directly from the evaporator, whereas with vavle control, the condensing unit is independently powered, and turns on/off based on the solenoid valve. Valve control is more common in the industry, and benefits from not having to run a power line from the evaporator to the condensing unit, but we do not recommend valve control for installations in temperatures below 30°F. Electronic control offers more precision, and allows the condensing unit to be placed in temperatures down to -20°F (with the addition of a compressor heater and fan cycling switch.)
Can the evaporator be located in a remote location and ducted to/from the wine cellar?
A: This unit's evaporator cannot be ducted; the evaporator must be installed inside the cellar. As an alternative, please consider our Air Handler 6500 Ducted System.
Can I install the entire unit inside the cellar?
A: No, the condensing unit must be located outside the cellar.
If I don't have sufficient space around the condensing unit, is that Ok?
A: The condensing unit generates hot air that must have sufficient space to dissipate, otherwise the unit will recycle its own hot air. The condensing unit cannot be ducted; it requires 12 inches of unobstructed space in front of the coils, and requires approx. 600-700 CFM of ventilation when installed in a confined space.
Does the evaporator include flare connections, or will I need to braze the connections to the line-set?
A: Flare connections are much more prone to leaks, and have been phased out over the years, replaced by fully-brazed connections. This is driven by the EPA and the focus on minimizing refrigerant leaks into the atmosphere.
We want to put a wood grill in front of the evaporator, what is the percentage of air flow that grill will need to have?
A: Our units require 1/2" minimum spacing, as well as a baffle behind the grill to separated the cold air discharge from the coil intake. We have seen problems with custom grills where there is a gap between the unit and the grill and it causes air circulation behind the grill resulting in coil icing. It is also important to note that the evaporator must be mounted to the interior cellar wall, not buried inside the wall. If it is buried inside the wall, the housing will require insulation, otherwise condensation and heat loss issues will occur.
Does the unit really need a dedicated circuit?
A: First, the background. Unlike our competitors, we build our cooling units with precision expansion valves, not cap tubes, which means that our cooling units aren't limited to a 30°F differential between the desired cellar temperature and the ambient temperature. Cooling systems with expansion valves are much more precise than cap tubes, and much more sensitive to low voltage conditions, which is why our units require dedicated circuits. When we say "dedicated circuit", we mean that the circuit shouldn't have any items that require heavy draws of electricity - eg other appliances, vacuum cleaners, big-screen TVs, blow-dryers - on the same circuit as the cooling unit. Lighting, computers or other low-draw items shouldn't be a problem on the same circuit.
Ratings & Reviews
Excellent unit far superior to competitors
by Charles Von Schmidt -
We had a failure in a 990 cf custom built cellar of a competitive unit. As a custom home builder the quality difference between the brands is substantial. The cellar Pro 6000 unit is obviously a piece of commercial refrigeration equipment the install was straight forward with heavy gauge materials. Immediately upon install the unit began preforming its job and brought the cellar down to the initial set point of 59 degrees and after changing the thermal mass of the wine bottles did something the competitor unit never did. It shut down and began cycling occasionally. Monday we will do the final instal check, adjust pressures, lower set point to 54 degrees and return the install sheet for review. High quality equipment, excellent pre sale service.
CellarPro 6000S Review
by Rich E
Good instructions to install, unit is still cooling down the cellar.
Good system-excellent support
by Steve Schloming
I'm a general contractor who was asked to renovate a very fine wine cellar. I chose this system after a visit to the factory- they happened to be close by. I saw high quality components and high value in the manufacturing process. We chose the 6000S because the evaporator fit nicely into the space allowed in our cellar. The latitudes and versatility of this unit allowed it to perform nicely in terms of cooling and humidity control even though it is somewhat oversized.
Installation was straight forward. I do recommend you find a subcontractor who is a refrigeration specialist, not just an HVAC guy who mostly does a/c.
More importantly, I was given great support before the purchase and installation, and when we did have a glitch, the folks at CellarPro were right there backing us up. Their warranty is underscored by their posture of being a collaborative team member. So, good value all around. The kind of people you want to work with.