CellarPro 1800XT Cooling Unit #1086
CellarPro 1800XT cooling units (1/6 Ton Nominal) are suitable for small wine cellars (up to 250 cubic feet), commercial applications and wine cabinets located in garages (in temperatures ranging from 50-95F).
Performance testing shows that this compact unit maintains optimal cellar temperature and humidity conditions more effectively than similar units from competing brands. 1800XT units also are significantly quieter than comparable units from other brands. Visit our Learning Center for data tables, performance charts and product comparisons among different brands.
CellarPro 1800XT units are sized to replace Breezaire 2200 and Wine-Mate 2500 cooling units. Please confirm equivalent dimensions and airflow prior to purchase.
All air-cooled refrigeration equipment requires fresh air intake to dissipate the heat generated by the cooling unit. The fresh air intake CANNOT come from the wine cellar space - it must come from space outside the cellar. Designed for indoor use only, 1800XT units can operate in environments ranging from 95F to 40F out of the box. To operate the unit in colder temperatures, please see modifications listed on the Options & Upgrades tab.
- This unit offers a choice of top or rear hot exhaust. If the unit's location does not provide sufficient room for airflow, you may need to purchase a rear duct kit.
- Adjustable humidity control combines a high-output compressor with flexible fan cycles to maintain a recommended level of moisture inside your cellar.
- Extra-large coils generate maximum cooling power.
- Commercial-grade Electrofin coating protects the evaporator coils from leaks and corrosion.
- Intuitive LED display panel mounted on the evaporator with digital programmable thermostat is simple and easy to use. Remote thermostat is available as an upgrade.
- Energy-saver mode, quick-chill mode, and auto-defrost cycle provide convenient solutions to common cellar needs.
- Temperature set point range is 47F to 62F when the cooling unit is properly sized.
- Unit operates with minimal vibrations and less noise than comparable units from competitors.
- Audible and visual alarms and maintenance-needed indicator protect the cooling unit and the wine cellar.
- 10-foot power cord exits from the rear and plugs into standard 110V receptacles.
- Common dedicated 15-amp circuit is required to power the unit.
- 3-amp electric receptacle is provided to run a small lamp.
- Removable steel case provides access to the internal components for servicing and repair.
- CellarPro's 5-Year Standard Warranty, the most thorough in the industry, protects the unit against manufacturing defects.
- An optional Enhanced Warranty (#1835) is available for additional protection.
- ETL Tested and Certified to rigorous UL Standards for safety.
Size: 18w x 16 1/2d x 10 1/2h (in)
Weight: 60 lbs
115V AC / 60 Hz
- Running: 3 Amps
- Startup: 20.1 Amps
- Requires: Dedicated 15-Amp Circuit
- Recommended: Surge Protector
Decibels: 47 dBA (Rear)
Capacity: 1456 BTUH @ 60F
Sizing Table: Click here to view sizing table
5 Years (Entire System)
Optional Extended Warranty sold separately.
Click on one of the following links for more information:
- Spec Sheet
- Sizing Table
- Owner's Manual
- Product Brochure
- Configuration Options
- Installation Diagrams
- Adjustable Humidity Chart
- Sound Level
- Monthly Operating Cost
- Front, Rear & Side Views
- Top & Bottom View
- Rear Drawings - As Ducted
- Compressor Heater #1727: protects the unit when installed in environments that drop down to 20F.
- Fan Cycling Switch #6972: supports the unit in temperatures below 20F and as low as -20F when combined with our compressor heater.
- Duct Intake Hood (Cold Side) #1932: permits the cooling unit to be placed directly above the cellar.
- Duct Hood (Hot Side) #7409: allows you to install the unit completely inside your cellar or in a small space with limited airflow. Includes an auxiliary fan, but no ducting.
- Duct Kit (Hot Side) #1439: same as the Duct Hood, this kit also includes 2 x 25-feet of 6-inch insulated (R-6) flex ducting.
Filters & Grills
- Use our filter & grill guide to find the cooling unit filter or duct filter and/or duct grill that is appropriate for your cooling unit.
Remote Control & Probe
- Remote Display #1603: lets you place the digital panel wherever you want, whether inside or outside the cellar. Includes 10 feet of wiring.
- Bottle Probe #1434: this remote thermostat with a 10-foot cord overrides the thermostat on the face of the cooling unit, and allows it to monitor air or liquid temperatures at various locations inside the cellar.
- Extension cords available in 25-foot (#1780) and 50-foot (#1781) lengths.
Other Options & Upgrades
- Condensate Drain Line: strongly recommended for wine cellar installations (but not required for wine cabinets), a drain line allows excess moisture to drain from the bottom (#7431) or rear (#1606) of the cooling unit.
- Condensate Drain Line plus Heating Element: combined with a drain line, we add a 100W heating element to burn of excess moisture. Available with bottom (#7432) or rear (#1709) drain lines.
- Power Cord Modification #1098: normally the cord exits from the rear of the cooling unit, which generally is outside the cellar; this modification moves the cord to the front of the cooling unit, so that it can be plugged into an outlet inside the cellar.
- Mounting Clips #1095: attached to the front of CellarPro 1800 Series cooling units, these clips are designed to be bolted to the ceiling inside the wine cabinet / cellar.
DID YOU KNOW?
Nobody protects your wine cellar better than CellarPro Cooling Systems! In the event your cooling unit fails and the failed components are covered by our warranty, we'll send a replacement cooling unit to you per the terms of our Replacement Unit Program
CellarPro Replacement Unit Program
If your CellarPro cooling unit fails and the parts that failed are still covered by warranty, we'll send a replacement cooling unit to you, as follows:
- Your cooling unit must be registered at CellarPro
- Your cooling unit must have been properly sized, installed and maintained
- Your cooling unit may not have been permanently modified, damaged or disfigured
- Replacement units are factory-refurbished cooling units with a similar build date as your original unit
- You are responsible for the shipping cost to send the replacement unit to you and return the original unit to us, and the cost (if any) to remove the original unit and install the replacement unit
- In order to send a replacement unit, we require a deposit, which will be refunded minus shipping costs upon the return and pending the inspection of the original unit
- If the original unit failed due to improper intallation or use, the failure is not covered by warranty and we will deduct the cost of the repairs from the refund of your deposit
A: For installations in environments below 40F down to 20F, we recommend adding our compressor heater (P/N 1727), which is included as standard equipment on all outdoor units. Below 20F, in addition to the compressor heater, we recommend adding our fan cycling switch (P/N 6972)
How do I choose between top exhaust versus rear exhaust? What about the fresh air intake?
The fresh air intake will always come from the rear of the cooling unit, and must pull air from OUTSIDE the wine cellar space - it must never be installed to pull air from inside the cellar. On 1800 Series cooling units, the hot air exhaust can exit from the top or the rear. Choose whichever configuration directs the exhaust to a space that is sufficiently large to accept the exhausted air, as long as the exhaust goes OUTSIDE the cellar and will NOT intermingle with the fresh air intake. If you plan to duct the hot side of the cooling unit, then the hot air will need to exhaust from the rear.
Does the unit really need a dedicated circuit?
A: First, the background. Unlike our competitors, we build our cooling units with precision expansion valves, not cap tubes, which means that our cooling units aren't limited to a 30F differential between the desired cellar temperature and the ambient temperature. Cooling systems with expansion valves are much more precise than cap tubes, and much more sensitive to low voltage conditions, which is why our units require dedicated circuits. When we say "dedicated circuit", we mean that the circuit shouldn't have any items that require heavy draws of electricity - eg other appliances, vacuum cleaners, big-screen TVs, blow-dryers - on the same circuit as the cooling unit. Lighting, computers or other low-draw items shouldn't be a problem on the same circuit.
Can the cooling unit be located in a remote location and ducted to/from the wine cellar?
A: These cooling units can be installed above the wine cellar when used with our front intake hood.
Does the unit need to be installed through the wall, or can I install the entire unit inside the cellar?
A: These cooling units can be installed completely inside the wine cellar when used with our rear duct kit (P/N 1439), which allows rear supply and return airflows from a temperature controlled environment OUTSIDE the cellar to be ducted (with insulated ducting to minimize heat transfer inside the cellar) up to 100 equivalent feet (50 feet per duct).
What if I don't have sufficient space behind the cooling unit for the hot air exhaust to dissipate?
A: The rear of the cooling units can be ducted to another location by using our rear duct kit (P/N 1439), which allows rear supply and return airflows from a temperature controlled environment OUTSIDE the cellar to be ducted up to 100 equivalent feet (50 feet per duct).
Do I need the condensate drain line?
A: If you are using the cooling unit in a sealed cabinet, you probably don't need the drain line. If you are using the cooling unit in a cellar, we recommend the drain line, which can be drained inside (bottom) or outside (rear) the wine cellar. Choose the 100W heating element to reduce drainage as it helps to burns off excess condensate before it reaches the drain line.
Ratings & Reviews
by Alex S.
I had to replace a failed cooling unit on my wine cellar and switched to the Cellar Pro 1800XT. I have two glass walls on my wine cellar and the old unit always struggled to keep up with the heat. The 1800XT was a breeze to install and does a great job. What was really impressive was how fast it cooled the cellar down. I am very pleased.
Keeps the Wine Cool!
by Mark L.
I've had my wine cabinet for 15 years, so this was the second time I had to replace the cooling unit and this was a drop-in replacement. Easy to install and it's up and running!
Great Product and Customer Support
by Micah M
The customer service was great. My 1800xt arrived on time and runs great. It is more quiet then I expected. I would recommend this product.
by Michelle M
I have had my 750 bottle Wine cabinet for 12 years. I just replaced the cooling unit (Breeazaire) with CellarPro's own brand. It's by far superior. The employees were very helpful and professional. I highly recommend their product and service!
Cellar Pro 1800XT
by Jay Butler
The folks at CellarPro were great to deal with.... Unit arrived on time and was quite simple to install. And it's performing Great!
Installing the unit was a breeze. I was worried that this would be a big project, but honestly, removing all the bottles of wine off the top rack to perform the changeout was the hardest part! It was very easy. The cooling unit had the cabinet at a perfect 59 degrees within a matter of hours. Great product and I'm very happy with it.
The unit is certainly better than the Breezaire I had. However, I have never been able to get it down to 55 degrees. It clicks on and off every few minutes, and temp. stays around 60-62. It would be nice to be able adjust the temp. to whatever temp you want.
by Thomas G. Zentner
The new unit arrived just before record breaking high temperatures came. So the installation in my garage was a real test. So far it has performed well. The installation was a bit tricky. The new grill on the front and the screws instead of rivits made the unit impossible to install from the back. I called service and they said that the front installation was easier anyway. With a bit of vasoline and some pushing, the new unit slowly moved into place. Even at 95 degrees, the unit is holding temperatures in a tight range, and is cycling "on" for a surprisingly short time.
by Gary Allen
Just recieved my new 1800xt unit and went thru the simple startup procedure, installed the unit and it cooled my cellar down in 8 hours. I highly recommend this unit as a replacement or for a new cellar, it may cost you a few more buck up front but it is well worth it in the long run. I replaced the previous brand twice in four years before I learned my lesson. Thanks CellarPro its cool in Dallas.
This unit is very quiet. Installation was easy, Great customer support answering questions before the order.
What a relief
by Steven R.
I replaced my existing Breezaire with the 1800XT. The lack of expected noise was a pleasant surprise and the airtemp stability is better than new. Easy to adjust to personal preference temp and humidity settings (really not necessary as the system is very adquate and ready to go right from the carton), this unit was just as advertised as a direct replacement for my Breezaire unit. I upsized by 40% as my cellar is in a very warm Southern California garage (where two daily driven automobiles share space). I followed directions to the letter, letting the unit sit for 24 hours and then bench running it for 1 hour to test the unit. Warning, the directions do not say to raise the unit when bench testing. Very necessary as otherwise one would block the return air.
Night and Day
I replaced a 5-1/2 yo Breezair 1060 that never really performed well. It is was spec'd to work for my 5200, especially in-doors. It struggled in hot humid weather and resulted in my having to raise the cellar's temperature to 62+, every summer. Then, it started failing even in cooler weather. I'm glad that I never upgraded to the noisy 2200, since they apparently had issues too. The 1800XT was an easy installation and I was done in about an hour. It hasn't been hot around here yet, but I can already tell that it will have no problem holding the temperature. The real test will come soon enough when our 6 months of 90+ weather and high humidity begins in a couple weeks.
Just bought this unit. Initially, it kept on giving me an error message that the condensing coils were over heating. I realized that the exhaust of extremely hot air from the unit was coming out right next to the intake!. So, I installed a piece of cardboard to re-direct the air away from the intake, and now the unit is working quite well, keeping my 900 bottle walk-in wine cellar at 56 degrees.
Recently purchased 2 1800 XT units as replacements for seven year old Breezaire 2200's
in a free-standing 2500 bottle cellar. The units are much quieter than the Breezaires and do
not run nearly as much to maintain the set 60 degrees. While more expensive than the
Breezaire, these are definitely an up-grade and should result in energy savings as well.
Great unit and easy to install
I bought this to replace the cooling unit that came with my Vinotemp which died after 3 years. What an improvement! This keeps the cabinet much cooler, and was SO easy to install. My only regret is that I didn't buy this in the first place.
by Brian P.
We recently purchased an 1800 XT as a replacement for the Breezaire 2200 unit for our European Country Model 5200 Wine Cabinet. (The Breezaire 2200 compressor quit after roughly five years of indoor use.) Some findings after a month of use:
1. The 1800 XT is much quieter than the Breezaire unit.
2. We love the humidity control of the 1800 XT, which is not available on the Breezaire.
3. We've noticed that the 1800 XT runs much less of the time than the Breezaire, indicating that it is putting out cooler air.
So Far So Good
by John O.
I have had the CellarPro 1800XT installed for about 4 months now. Initially it seemed to be running quite a bit. I called the company and one of the owners answered and gave me tons of advice. Wow. Talk about customer support.
by Billy G.
Great unit, easy installation, converted a closet to a wine cellar, does a great job so far
"Replacement" that is better than the original!
by Mike Petonic
We recently bought the 1800 XT because our Breezeaire 2200 stopped working after 10-11 years. It was at least a couple of hundred dollars more expensive than the 2200, but well-worth it because a) it's a lot quieter than the 2200, and has more cooling capacity. We don't have air conditioning in our condo in San Francisco (who does?) and on those occassions when it nears 100 degrees, the 2200 was taxed and the temperature of the cellar rose more than I was comfortable with. The extra $200 is well spent insurance against hostile storage conditions.
Also, the partners are supremely customer focused and knowledgeable. They accomodated delivering the unit to a partner's house in San Francisco, while I picked it up one morning. Unusual, and very much appreciated.
If you're considering this unit, and have an application for it, I would highly recommend it. It's a well-built unit, quiet, and I have no doubt that the company backs up their products, should it ever need servicing.